Hvac Blower motor problem
My hvac blower started making a noise that is progressively getting worse. I removed the motor and ran it without the load(blower). No noise.
Than I add the blower cage to it and that's when I noticed that there is a slight play in the motor shaft. This play only exists in one line(let's call it east to west and west to east). The play does not exist in any other direction. Even if I spin the shaft to a different position the play still exists in the east to west direction.
When I ran these tests the motor is placed on a flat surface and all 4 feet are firmly placed on the table and stable.
Is this play symptomatic of a problem with the motor?
HVAC Blower motor problem.
The shaft will always have a slight movement in and out from motor. IF the movement is more progressed in and out OR the movement is side to side, the motor is on its way out.
|All times are GMT -7. The time now is 11:39 PM.|
Powered by vBulletin® Version 3.6.4
Copyright ©2000 - 2015, Jelsoft Enterprises Ltd.
Content Relevant URLs by vBSEO ©2011, Crawlability, Inc.