Central AC is not reducing humidity
Hi Guys. Thanks in advance for any advice.
We turned on our AC yesterday. The system is blowing cold air and properly regulating the temperature but the humidity is stuck in the mid 60's which makes it very uncomfortable.
The unit was on about a week ago and was working fine then we shut it off when the weather got a little nicer.
I checked the drain hose from the unit in my basement and there was hardly any water coming out of the unit, which confirms my thought that its not pulling out the humidity. The hose itself is pretty dirty and I was thinking about making sure it isn't clogged. Would a clogged drain hose be enough to cause the system not to pull the moisture from the air?
The system is original which puts it at about 23 years old (I'm saving for a replacement). I just wanted to check in with you guys before I pay to have a tech come out. I'm a pretty handy guy and I can fix most things.
Would a clogged drain hose be enough to cause the system not to pull the moisture from the air?
It could but I would expect that the drip tray that runs around the bottom outside of your A coil would overflow and you would see water dripping out of the furnace somewhere. But this would depend on you set up.
The reason I say this is that the surface area of the water in the drip tray is fairly small so I do not think that the air going through the system would be able to pick up enough moisture to keep the humidity that high. But stranger things have happened.
Open the system up so you can check you A coil and the drip tray.
there is a possibility that the underside of the A coil is so dirty that it is holding the moisture and not letting it drain off.
check the filters in your air conditioner
This sounds to me like the condensate line is plugged,..... normally the excess would run over the edge of the drain pan and make a big mess
Overcharged unit if someone worked on it recently
Bad txv - not found on all units, other units use a fixed metering device instead
|All times are GMT -7. The time now is 12:21 PM.|
Powered by vBulletin® Version 3.6.4
Copyright ©2000 - 2018, Jelsoft Enterprises Ltd.
Content Relevant URLs by vBSEO ©2011, Crawlability, Inc.